Z316.5-04 (R2009) - Fume Hoods and Associated Exhaust Systems
What Others Bought
CAN/CSA-Z107.56-06 (R2011) - Procedures for the Measurement of Occupational Noise Exposure
CAN/CSA-Z317.2-10 - Special requirements for heating, ventilation, and air-conditioning (HVAC) systems in health care facilities
C22.1-12 - Canadian electrical code, part I (22nd edition), safety standard for electrical installations
CAN/CSA-Z94.2-02 (R2011) - Hearing Protection Devices - Performance, Selection, Care, and Use
Z94.3.1-09 - Selection, use, and care of protective eyewear
B51-09 - Boiler, pressure vessel, and pressure piping code.
Z8000-11 - Canadian health care facilities
C22.1-12 PACKAGE - Consists of C22.1-12, Canadian electrical code, part I (22nd edition), safety standard for electrical installations; CE code pocket reference book and the C22.1HB-12, CE code handbook, an explanation of rules of the canadian electrical code, part I
PrefaceThis is the second edition of CSA Z316.5, Fume hoods and associated exhaust systems. It supersedes the first edition, published in 1994.
1. Scope1.1 This Standard applies to all types of laboratory fume hoods, except for recirculating fume hoods.
1.2 This Standard specifies (a) safety requirements for fume hoods; (b) test methods for assessing fume hood performance; (c) requirements for the selection, use, and maintenance of fume hoods; (d) requirements for the education of fume hood users and maintenance personnel; and (e) requirements on information to be exchanged between suppliers and users of fume hoods to ensure that installation, function, and maintenance are compatible with the intended use.
1.3 This Standard does not address detailed design considerations such as fan selection and duct and stack velocities. This Standard does not apply to biological containment cabinets. Note: Requirements applicable to the installation and field testing of biological containment cabinets are found in NSF/ANSI 49.
1.4 Users of this Standard should note that fume hood requirements are also established by regulatory authorities. Note: Other fume hood requirements can be found in, e.g., the National Building Code of Canada, the National Fire Code of Canada, the Canadian Environmental Protection Act, and the Nuclear Safety and Control Act.
1.5 In CSA Standards, "shall" is used to express a requirement, i.e., a provision that the user is obliged to satisfy in order to comply with the standard; "should" is used to express a recommendation or that which is advised but not required; and "may" is used to express an option or that which is permissible within the limits of the standard. Notes accompanying clauses do not include requirements or alternative requirements; the purpose of a note accompanying a clause is to separate from the text explanatory or informative material. Notes to tables and figures are considered part of the table or figure and may be written as requirements. Legends to equations and figures are considered requirements.
1.6 The values given in SI (metric) units are the standard. The values given in parentheses are for information only.
GST REG No R119441681
QST REG No R1006017360